UPS Maintenance Bypass Switch 16A MBS Rack Mounted MBS 1-3kVA FREE UPS Delivery
F you need to perform maintenance on a UPS, such as replacing batteries or upgrading the UPS then you may need to maintain power to the equipment while you perform this operation. With the bypass switch you are able to isolate the UPS and continue to feed power to the load from the mains power supply. Any questions please feel free to ask. UPS Maintenance Bypass Switch 16A MBS Rack Mounted MBS 1-3kVA.6 x IEC C13, 1 x IEC C19 Outputs. Same Day Dispatch with UPS. The purpose of the bypass switch is to provide continuity of supply during maintenance operations, although I must caveat what this means. The switch has 2 positions, Normal and Bypass; This is a break before make switch. This means that there is a slight loss of power to the load when switching. This is in the order of 2 mains cycles maximum. Usually, IT equipment does not have any problems with such fast switch overs. This also prevents accidentally back-feeding power from the mains into the output of the UPS. Why you may require one of these? If you need to perform maintenance on a UPS, such as replacing batteries or upgrading the UPS then you may need to maintain power to the equipment while you perform this operation. A small price to pay for reduced downtime of users and dirty power shutdowns.
Rack Ears / Wall mount lugs. The unit comes supplied with the rack ears on the front of the unit for connection to a standard 19in rack. To wall mount the maintenance bypass switch, remove the rack ears with a pozi screwdriver and connect them to the rear of the unit using the same screws. Remember to use suitable wall supports and screws/washers to cover the rack mount holes in the rack ears. 6 x IEC C13, 1 x IEC C19.
- Features: Fused
- Unit Type: Unit
- Colour: Black
- Model: MBSRACK 1-3
- Voltage Compatibility: 230 V
- Unit Quantity: 1
- Brand: Certa Rack
- Type: Power Distribution Panel
- Maximum Input Current: 16 A